- Measuring of the pressure-differences of gases
- 8 measurement ranges between 0-5000 Pa
- Medium temperature: up to 60 °C
- 4-20 mA two-wire transmitter
- Intrinsically safe
- LCD display
- IP 65 protection
The DT7000 Intrinsically Safe Differential Pressure Transmitters are suitable for measurement differential pressure of dry non corrosive gases in even the most hazardous plant areas (zone 1, zone 2).
The instruments provide a 4-20 mA current signal, proportional to the pressure connected to their pressure ports.
The DT7000 presents the measured pressure values on an LCD display too.
Eight different measurement ranges are available from 0-50 Pa up to 0-5000 Pa, but user defined measuring ranges are also available. The temperature of the measured medium may vary between -20 °C and +60 °C.
The pressure to be measured can be connected to the transmitter via pneumatic tube 2 × Ø4 mm inner diameter.
The die-cast Aluminium housing has IP 65 protection.
|Intrinsical safety data:|
|Certification:||BKI 04 ATEX 145 X|
|Protection marking:||II 1/2 G EEx ia IIC T4|
|Ui [V]||Ii [mA]||Pi [W]||Ci [nF]||Li [uH]|
|Ranges:||see the table below|
Special ranges that differ from the above are also available upon request.
|Output signal:||DC current, proportional to the measured pressure|
|Response time:||0.5 ms (10-90%)|
|Display:||3.5 digits, + or – sign, decimal point|
|Display unit:||LCD, 12.7 mm with character height|
|Loop power supply voltage:||12-28 VDC|
|Operating temperature range:||see the table below|
|Ambient temperature||Medium temperature|
|-20 °C <Ta< 60 °C||-20 °C <Tp< 70 °C|
|Relative humidity:||90% (max., non-condensing)|
|Place of installation:||potentially explosive area|
|potentially explosive area|
|Noise emission:||Group 1, Class B|
|Data in general:|
|Housing:||die-cast aluminium, KO36 steel connection|
|Process connection:||2 × Ø4 mm pneumatic tube|
|Electrical connection:||3-pole connector DIN43650 / IP 65|
|Connection cable:||0.25-1.5 mm2|
|Dimensions:||127 × 85 × 58 mm (width × height × depth)|
|Detailed information see in operating instructions. The Manufacturer maintans the right to change the technical data!|